Do you get a mildew-type odour when your air conditioning system first starts up?
From information gathered over many years, most professionals agree the "Dirty Sock Odour" is caused by a bacteria that collects and grows on the indoor coils of heat pumps and air conditioners.
Complaints normally surface when heat pumps go into defrost, or when systems are run in heating for a brief time then switched back into cooling. The bacteria or odor collects and grows on the coil during this heating time and is released all at once when the indoor coil gets cool and damp. Heat pump owners notice the odour when the system goes into defrost, usually when the outdoor temperature dips below 4 degrees C. Heat pumps and air conditioners experience the problem, when the air conditioner is turned back on after the heating has been used. Our climate can require heating in the morning and cooling in the afternoon. This is a perfect condition for a complaint to surface.
Most people describe the odour as a musky, dirty, locker room smell. The problem is similar to an odor that is blown out of a car air conditioner when the AC has not been used for a while.
It is very important to properly identify the problem before any action can be taken, since many odour problems are incorrectly labeled as a dirty sock problem. Eliminate dirty drain pans holding water, drain lines connected to plumbing systems without adequate traps or dry traps, return air leaks in ductwork or chases, or dead animals in ductwork or near the living space. If the odor is present ALL the time, especially during heat, the problem is NOT a dirty sock syndrome complaint. Dirty sock complaints only smell when the indoor coil gets cool and the bacteria releases its odour into the air stream.
The problem itself is sporadic and limited to isolated households and is somehow related to the living style or products in the home or office. After removing a "stinky" unit from a complaint house, the unit can be cleaned and installed elsewhere without a complaint surfacing. Changing the brand of equipment is met with a similar lack of success. In one instance a complaining customer underwent a divorce and when one of them moved out of the home, the problem went away.
Much effort and expense has been given by the industry to research and solve this odour, Anotec spending tens of thousands of hours in their effort. In an effort to determine what in these homes or offices could create the complaints, Anotec has taken numerous air samples looking for a common denominator with no successful results.
Once the problem has been properly identified, action can then be taken to resolve or reduce the complaint, starting with a thorough cleaning of the evaporator coil with a non-acid coil cleaner. Cleaning will bring the system back to normal and will usually prevent a complaint for the rest of the heating season. Some systems cleaned early in the season or those having more of a problem may have repeated problems during the same season, especially if the weather conditions force a system back and forth from heating to cooling. The majority of complaints are resolved with a thorough cleaning.
If the coil cleaning does not resolve the complaint to a satisfactory level, the next suggested action would be to clean the coil again and apply a coating of Anotec SFS1121, a special solution designed to continuously protect coils from fouling caused by airborne contaminates. If seasonal cleanings or the application of this does not resolve the complaint, as a last resort, your coil may need to be replaced.
Dirty Sock Odour complaints can be quite emotional and are generally aimed at the equipment manufacturer.
While researching this topic, I asked a relative for some practical advice to rid my house of cigarette smoke. Their answer was immediate an...
A question always asked around the net can be answered visiting http://www.kaufda.de/umwelt/carbon-neutral/1-tree-1-blog-how-it-works/ ...
New 24-hour hotline set to help stink-fighting Kingston residents - Local News - News - Moorabbin LeaderNew 24-hour hotline set to help stink-fighting Kingston residents - Local News - News - Moorabbin Leader : "DISAFFECTED residents in Cl...
Review A gripping, brilliantly told tale of the secret and deadly struggle between American national security and the kings of the oce...
A Delaware corporation and a numbered Nova Scotia company are suing a Nova Scotia couple for the costs of remediating two Bedford properties...
Booming Waikato milk production has caused more complaints about smelly dairy waste, this time at Waharoa, near Matamata, where Open Country...
A mixture of plant oils, bacterial spores and ozone is responsible for the powerful scent of fresh rain. Image via Wikimedia Commons/Juni ...
I recently moved into a new apartment. The refrigerator has an ice-maker, but the ice from it tastes musty. I let the bucket fill up. Then I...
The Hindu : Cities / Visakhapatnam : Steps being taken to contain industrial pollution in city, says APPCBThe Hindu : Cities / Visakhapatnam : Steps being taken to contain industrial pollution in city, says APPCB
Types of Perfume (Determined by the amount of solvent mix and fragrance oil ) are these: 1. Perfume has 20-40% aromatic compounds; 2. Eau...